Customer called to see if we could get her basement light working. We arrived quickly then diagnosed that the problem was actually a faulty flood control pump located in her front yard which was on the same circuit as the basement lights. We replaced a 13 year old pump and the electrical outlet within the pit, and installed a new circuit breaker within the basement panel as a precaution.
We saved her $125.00 in material and an additional $165.00 in labor!
When your home or office needs cost-effective solutions – please call us! @ 847-636-0771